Comfort Control has been the reliable company for value heating and cooling in Alpharetta, GA and the surrounding areas since 1992. Read our reviews from Alpharetta, GA to see how our craftsmanship, professional training and customer service has provided complete satisfaction for our heating and air conditioning services.
for Alpharetta, GA
Our Reviews by City
As always, great service from Vu.
DONNA PHILLIPS - Alpharetta, GA
DARYL - Alpharetta, GA
MARK - Alpharetta, GA
THOMAS - Alpharetta, GA
Vu is a very professional and personable technician who quickly diagnosed and corrected our problem. It was a weekend call and he was able to make it to our house around noon time. Very good response and resolution of our problem.
Response from Comfort Control Heating & Air:
Thanks, Thomas! We're glad you had a good experience!
On time, with good service
Mike - Alpharetta, GA
MARK - Alpharetta, GA
Expert Tech and Great Service
JOHN - Alpharetta, GA
Ta is all about service and goes beyond what you would expect from any company!!
Happiness is a Warm House !!!
THOMAS - Alpharetta, GA
Seth did a great job in analyzing our heating problem and getting it fixed quickly. Same day service and he called beforehand to say that he would be able to see us earlier than anticipated. Very thorough explanation of the problem and solutions. Always thrilled when a company can see you the same day that a problem arises and get your heating system operational when the cold weather arrives. Great Job !!!
DAVID - Alpharetta, GA
JAMES - Alpharetta, GA
BARBARA - Alpharetta, GA
Tamara - Alpharetta, GA
Reece is very professional and let me know the status of my units as well as gave me alternatives as far as replacing my systems.
We ran a 8â€ supply duct into a bedroom on the right back corner of the home for $425. We took off a basement line from a disconnected Y and respliced the torn ductwork without the basement line for a additional $100.
1 system furnace prepaid on new basement system. Tested and system is heating normal
No heat basement system. Found bad furnace blower motor, system is old and needs to be replace. Owner just wants repairs. Replaced with new motor,new motor controller and new thermocouple. Tested and system now heating normal
Signed up for new Comfort Club Membership. Found main floor system with the top louvers door at the lower blower compartment section of the furnace. Swapped doors and the furnace is now safe to use. found worn ignition, weak flame safety sensor, and weak blower motor controller. Owner wants to wait. 3 system heating normal
Replace both airhandler heating element relay and control board. Test and and new control and relay operating normal.
No heat downstairs. Check and find damage furnace power switch. Repalce main power switch for upstairs and downstairs system. Both heating furnace operating at this time.
Repalce lennox gas valve under warranty. Test new valve and operation. System operating at this time.
Completed tuneup on 2015 furnace. Changed 20x25x1 filter. checked all electrical, mechanics and safety devices. Unit is operating normal at this time.
Performed 1 System Maintenance. The furnace is heating properly at this time.
2 furnace pm check complete. Did not change filters. Found main level ignition system and flame safety worn, recommend replacing next year. Upstairs blower motor controller is very weak, recommend repair. Cleared barometric tubing. Changed main level humidifier's water panel. Systems are heating at this time. Customer declined repairs.
Gas valve is stuck closed. After purging the gas line and several attempts. The gas valve stays open for short periods of time. This problem will keep occurring. This furnace is 3 years old so the valve itself is possibly still under warranty. If so then the part will be deducted from the price above. The homeowner would like to wait on the repair and call the office on Monday.
Replaced blower motor capacitor and flame safety sensor. Furnace is now heating properly.
Replace airhandler control board under warranty but system airhandler still not operating due to faulty element relay. Replace to order and come back to replace under warranty.
Renew and complete heating preventative maintenance check. Find heating system operating normally. Change filter, check safety and operation.
Homeowner purchased 1 System Maintenance Agreement. Performed 1 System Tune up. Furnace is 14 years old. I found a weak blower motor capacitor and a weak flame safety sensor. I recommend both be replaced at a minimum. Homeowner is also interested in Zoning her home.
Heating Repair. Find zone #2 AA8466 thermostat faulty. Replace thermostat under warranty. System and tstat are operating normally at this time.
Furnace Repair. Found faulty control board. Need to order a new board and come back to replace under warranty.
Replaced air handler board under warranty. Will return tomorrow to replace sequencer.
Signed up for a new maintenance plan. Replaced 3 clogged filters. Found upstairs with worn ignition and weak flame safety sensor, replaced both parts and heating normally. Main floor system heating normal. Both humidifiers were disconnected from the water supply, power supply for humidifier and humidistat. Needs to upgrade to a steam humidifier for proper humidity level and better efficiency due to the size of the house. Master bedroom ignition is getting worn and has weak flame safety sensor. Master system heating normally.
Completed maintnenace on both systems. Checked all electrical, mechanical and safety components. Both units are operating normal at this time. Needs new filters in spring time did not change this visit.
Air handler board is not powering heat strips. The board will need to be replaced.
The Ecobee Thermostat is not sending power to the furnace. Homeowner wants to install his own and has declined repairs at this time. Purchased 2 System Maintenance agreement.
Completed maintnenace on 3 systems. Upstairs and main floor furnace are 20 years old, both transformers are over heating and could cause issue in near future. Basement system is brand new and operating normal at this time.
Performed 1 system heating maintenance. Upstairs supply plenum has live black mold growing. Recommend U/v light to kill mold spores and bacteria. Voltage absorbsion system reading below acceptable ranges and needs to be replaced. Igniter showing advanced signs of wear. System operating properly at this time
1 furnace preventative maintenance check complete. Changed filter. Tested mechanical and electrical components, found worn ignition system. Likely to break, recommend repair. Found worn flame safety. The system has no water safety. The HVAC system is heating at this time. Renew 1 system Comfort Club plan. Replaced ignition system and flame safety system. Recalibrated furnace for better heating efficiency.