Comfort Control has been the reliable company for value heating and cooling in Atlanta, GA and the surrounding areas since 1992. Read our reviews from Atlanta, GA to see how our craftsmanship, professional training and customer service has provided complete satisfaction for our heating and air conditioning services.
for Atlanta, GA
Our Reviews by City
KUMAR - Atlanta, GA
High Performance as usual
Ed - Atlanta, GA
Arrived on time. Explained what needed to be done. Left the place clean an functioning
Complete 2 heating pm check. Change both filter. Check and find both 17 year old furnace operating but not efficient and worn flame sensor. Downstairs ignition badly worn. Complete 2 flame safety renovation HM15C with new ignition, flame sensor and complete combustion calibration. System operating at this time.
2 system furnace prepaid pm. Replaced air cleaner upstair and replace downstair filter. Both system heating normal at this time.
Completed maintenance on Air Handler . System has mold starting to grow in the Air handler .Reccomend Apco Air Purifier. Coil is rusting and could cause issues in the future. Air movement system is dirty causing stress on the blower motor. Reccomend a deep clean on the air movement system. Heat pump is operating normal at this time. All electrical components are operating normal at this time. System is heating normal at this time. Customer is going with installing the Apco Air Purifier. Completed install and Apco is operating at this time .
1 system furnace pm check complete. Changed filter customer provided. Did a complete combustion analysis and system is operating at safe co levels. Tested mechanical and electrical components, all in good shape. Customer's humidistat has manufacturer defect, office will schedule time for us to come back out and put a new one in aprilaire 60.
Upstair system making weird noise, tested and working normal. Only sound is air noise when the motor ramps up.will be a service charge next time