Comfort Control has been the reliable company for value heating and cooling in Atlanta, GA and the surrounding areas since 1992. Read our reviews from Atlanta, GA to see how our craftsmanship, professional training and customer service has provided complete satisfaction for our heating and air conditioning services.
for Atlanta, GA
Our Reviews by City
Winter service great
STEPHEN - Atlanta, GA
Very Dependable Service
MICHAEL - Atlanta, GA
Have used Comfort Control for years. Very dependable and reliable service. All Techs are very polite and on time.
MARIA - Atlanta, GA
Always on time, explains everything very well and really like that we have the consistency of the same technician each time.
KUMAR - Atlanta, GA
High Performance as usual
Ed - Atlanta, GA
Arrived on time. Explained what needed to be done. Left the place clean an functioning
Sealed dryer vent at roof with aluminum vent tape.
Sealed dryer vent at roof with aluminum vent tape.
Checked mini split and system is operating normal at this time. Found bad low and high air pressure switch on furnace. Replaced both pressure switches and unit is operating normal at this time. Signed up for new maintnenace plan and completed maintnenace on 2010 ruud furnace. Unit is operating normal at this time. Recommend uv light to kill mold growing in coil. Recommend duct cleaning and blower wheel cleaning.
2 furnace pm check complete. Washed upstairs filter. Main level filter kit will need replacing next visit. Filter kit # x8795, order from Lennox. Tested mechanical and electrical components, all in good shape. Replaced upstairs humidifier water panel. Systems heating normal at this time.
3 heating system pm check complete. Changed main level and upstairs filters. Did a combustion analysis on main level and upstairs furnaces. Upstairs furnace has good combustion readings. Main level furnace combustion readings show high oxygen levels and that it is operating at a lower efficiency than what it is supposed to operate at, recommend recalibration. Main level blower motor controller is running weak, putting a strain on blower motor. Recommend repair. Systems are heating at this time. Replaced blower motor controller and recalibrated main level system.
1 system furnace prepaid. Air cleaner good, checked electrical and safety switches all ok at this time. Found worn ignition and flame safety sensor getting weak. Owner wants to replace ignition for now.Overall system is heating normal
2 system furnace prepaid pm.replaced filters,checked electrical and safety switches all ok at this time. Installed 2 c0 detector for upstair and downstair system. Both system heating normal at this time. Owner will do duct cleaning for both system. Will let office call to schedule
1. installed shut off valve and adjusted condensate drain line in attic furnace 2. installed T/P valve on water heater drain 3. Corrected water heater vent slope to comply with standard of one-quarter inch per foot 4. removed unused A/C disconnect and wiring outside 5. HVAC units are current on all service requirements and do not have any outstanding recall notifications
Performed 2 system heating maintenance. Upstairs blower wheel has accumulated a significant amount of dirt and grime and needs to be cleaned to restore balance and efficiency. Main level unit needs combustion calibration. Furnace is over fired and kicks off on high limit. Performing combustion calibration today and performing blower wheel cleaning in spring time. All 3 systems operating normal at this time.
Zone 3. 2 system furnace prepaid. Replaced filter,checked electrical and safety switches all ok at this time. Combustion test all within range. Suggest to add uv light for bacteria and mold prevention.both system heating normal
Completed tuneup and changed filters. Found very dirty blower wheel and weak flame sensing system. Customer does not want anything at this time .
The Lineset cover had fallen off at the two highest places. I screwed the cover back on many times. This is all under full warranty.
Complete 2 heating pm check. Change both filter. Check and find both 17 year old furnace operating but not efficient and worn flame sensor. Downstairs ignition badly worn. Complete 2 flame safety renovation HM15C with new ignition, flame sensor and complete combustion calibration. System operating at this time.
2 system furnace prepaid pm. Replaced air cleaner upstair and replace downstair filter. Both system heating normal at this time.
Completed maintenance on Air Handler . System has mold starting to grow in the Air handler .Reccomend Apco Air Purifier. Coil is rusting and could cause issues in the future. Air movement system is dirty causing stress on the blower motor. Reccomend a deep clean on the air movement system. Heat pump is operating normal at this time. All electrical components are operating normal at this time. System is heating normal at this time. Customer is going with installing the Apco Air Purifier. Completed install and Apco is operating at this time .
1 system furnace pm check complete. Changed filter customer provided. Did a complete combustion analysis and system is operating at safe co levels. Tested mechanical and electrical components, all in good shape. Customer's humidistat has manufacturer defect, office will schedule time for us to come back out and put a new one in aprilaire 60.
Upstair system making weird noise, tested and working normal. Only sound is air noise when the motor ramps up.will be a service charge next time