The residents of Auburn, GA have considered Comfort Control a dependable company for heating and cooling services since 1992. Read how we provide top quality heating and cooling practices and continue to earn five star reviews in the Auburn, GA area.
for Auburn, GA
Our Reviews by City
Gave estimate for a mini split system for garage turned into a room. $4087 and a zone system with adding 2 supply ducts and one return to the garage $3778 Customer seems like he has no money for this project.
Completed maintnenace on heat pump system. Unit is operating normal at this time. Recommend attic insulation it is very low below beams.
1 heatpump pm check complete. Changed filter. Programmed thermostat to run heatpump and aux heat together instead of separate for better heating efficiency. Tested mechanical and electrical components, all in good shape. System is heating normal at this time.
Heating Repair. Reprogrammed thermostat to utilize heat pump and aux heat at the same time. Unit outside was making noise due to fan blade hitting plastic shroud slightly. Adjusted fan blade and tightened plastic shroud and noise stopped. If the problem presents itself again, we will replace fan blades and shroud under warranty. The system is heating at this time.
No heat main system. Found heatpump system freezing outside. System low on freon and found bad heatstrips kit. Needs more attic insulation and the family room side has no attic insulation. Charged system and heating only on heatpump with supply air of 88 degree. Needs new heat strip kit for proper heating. Owner just wants to add freon for now and let us know about heat strip kit and attic insulation. Have not paid
Performed 1 System Maintenance. I recommend updating the infinity touch control. Current infinity Tstat is having to be rebooted to have a visible screen. Homeowner is also interested in a laundry pro and an electric tankless water heater. Would like to have work done possibly all at once at the beginning of the year.
Performed 1 system heating maintenance. System needs surge protector. Wired directly to breaker panel. U/v light needed to clean coil. Blower wheel needs to be cleaned badly. System is very dirty considering its age. If recommended fixes are not performed system life expectancy will drastically be reduced.
1 heatpump pm check complete. Changed filter customer provided. Tested mechanical and electrical components, all in good shape. Evap coil is rusty. System is heating normal at this time.
Low voltage fuse blown. Replaced fuse, system operating properly at this time.
Performed 1 system heating maintenance. Heating operating properly at this time. Heat pump systems do not put out a temperature the same as gas furnaces do therefore the heat will be a slower process. Auxiliary heat required for faster healing.
1 furnace pm check complete. Left customer with replacement filter. Did a combustion analysis on system and got good readings, system operating at 92 % efficiency. Static pressure is good. Recommend recalibration to increase furnace efficiency. Recommend Apco air purifier for improved air quality. Recommend surge protector to protect furnace from power surges. System heating normal at this time.
System is heating normal at this time. Reccomend a deep clean on the air movement system to take stress off the blower motor.
1 System heat pump tune up complete. Ran and tested heat strips, they are operating properly. Tested mechanical and electrical components, all in good shape. Reran duct from supply to basement, and system is functioning properly now. Insulation levels are not up to code, recommend blowing in more insulation to help with better utility bills and system efficiency.
Performed air flow test, checked over entire job and made some corrections in system operation. Will need to return to replace ductwork in kids room.