The residents of Braselton, GA have considered Comfort Control a dependable company for heating and cooling services since 1992. Read how we provide top quality heating and cooling practices and continue to earn five star reviews in the Braselton, GA area.
for Braselton, GA
Our Reviews by City
Provided Great Service
GERALD - Braselton, GA
Very efficient and arrived on time for appointment
JOSEPH - Braselton, GA
BOB - Braselton, GA
Seth was on time and completed the work in a short amount of time. He answered questions around a future new HVAC system without pressuring to do it now.
Warranty no heat call. Zone board needed to be configured. System heating properly at this time
System is heating at this time . Heat pump is showing pit marks on the voltage distribution system. Reccomend replacing because it could get welded shut causing the compressor to run none stop .
System 3 Ton upflow 14 SEER Amana 90% Gas furnace 80,000 BTU B Width 10year parts warranty 2year Labor Warranty Outdoor pad Safety pan switch Overflow switch Condensate pump 8466 Tstat
Performed 2 system heating maintenance. Recommend insulation blown into attic to increase R-value. Rafters are exposed. Attic stair tent needed upstairs to prevent heat loss. Both systems operating normal at this time.
Replacing system this Wednesday 18th,2017. On Schedule for 8am. System is leaking refrigerant no repairs were done.
provided estimate for 3 full Amana Systems.
System need water safety switch. In the case of a water leak, drywall could be damaged. Run capacitor for furnace blower motor is weak and needs replacement. Open clean out pvc tee. The system needs e-z flow switch. Repaired all recommendations.
Completed maintenance on 2 heat pumps. Found voltage distribution system on bonus room unit with contact points starting to get pitted. Units are heating normal at this time.
Completed maintenance on system . Found mold starting to grow in the air handler. Reccomend a Apco Air Purifier to kill the mold and to purify the breathing air . System is hearing normal at this time.
Replaced 4 thermostats with aprilaire 8466.
No cool upstair. System is low on freon, charged system and cooling normal at this time. Owner will wait after the other house close to see which route they wants to do
No cool, check and find Amana heatpump not operating due to low charge. Check and find system leaking at discharge line connect to service valve port line. Need to recharge system. Give customer estimate to repair system. System also 14 year old, suggest to upgrade due to phase out equipment from EPA.