The residents of Johns Creek, GA have considered Comfort Control a dependable company for heating and cooling services since 1992. Read how we provide top quality heating and cooling practices and continue to earn five star reviews in the Johns Creek, GA area.
for Johns Creek, GA
Our Reviews by City
Guest room system Model number for air handler fy4anf018 Serial number for air handler 0610a70703 Price is $1938 Collected $500 deposit so remaining balance after install is $1138
3 heating system pm check complete. Changed upstairs and guest house filters. Found guest room system shutting off on low pressure lockout due to it being void of refrigerant. Having no refrigerant in the system indicates a major leak. Recommend upgrading system. Found main level/ upstairs furnace with very high, unsafe levels of carbon monoxide, recommend recalibration to reduce co levels down to safe levels. Furnace also has worn ignition system and weak blower motor controller. Basement system is also going off on low pressure due to it being void of refrigerant. Replaced blower motor controller and ignition system, and recalibrated co levels from 133 ppm down to 22 ppm. Customer is going to replace guest room system's evap coil for $1938, office will call to schedule. Customer also needs Garrett to come out for estimate on basement system replacement. Model number of airhandler we will replace coil in is fy4anf018, serial number is 0610a70703, product number fy4anf018000aaaa. Colle