Suwanee, GA has turned to Comfort Control since 1992 for professional heating and cooling repairs, installations and maintenance. Check out these reviews and see how we deliver heating and cooling that residents of Suwanee, GA turn to us for again and again.
for Suwanee, GA
Our Reviews by City
John - Suwanee, GA
Reece as always a true professional. Timely, efficient, neat and thorough. Thank you
TRACI - Suwanee, GA
LETICIA - Suwanee, GA
Great professional service. Prompt and curtious.
STEVE - Suwanee, GA
STEVE - Suwanee, GA
Great service .
David - Suwanee, GA
Hard workers very clean job.
Great service. Nice people.
Sandeep - Suwanee, GA
Tom and Comfort Control staff were excellent and provided professional and prompt service.
NICK Mesechoff - Suwanee, GA
I would highly recommend this company for any heating and cooling needs. Phillip was more than professional and courteous.
Response from Comfort Control Heating & Air:
Thanks, Nick, for the kind review and for being such a great client!
Tune up was a breeze!
JON - Suwanee, GA
Fast and helpful service.
TAMMY - Suwanee, GA
My technician Vu has been servicing my home for many years now. My two systems were installed 8 years ago. Vu was one of my original installation technicians and has serviced my account on numerous occasions. Vu is very professional and knowledgeable about his job. He takes great pride in his work, explains everything he is doing and why he's doing it. I'm always amazed at the level of service Comfort Control provides. The owner, technicians and office staff all go above and beyond to take care of business!
Bob - Suwanee, GA
GENA - Suwanee, GA
Robin - Suwanee, GA
Although Vu was 2.5 hours late from Our scheduled time, he was fast, friendly and very helpful in fixing our issue.
JAMES - Suwanee, GA
Paul conducted himself is a personal and professional manor. In my career I was a service manager for the office equipment industry. I would have been proud to have him representing our company out in the field.
Exellent service repair man . Very knowlegable
DAVID - Suwanee, GA
Highly reccomend Ta Kim
DOUGLAS - Suwanee, GA
Great and Prompt Service!
Virginia - Suwanee, GA
Fred - Suwanee, GA
Super SUPER Technician!!!!
Howard - Suwanee, GA
I could not have had better service call if I had personally hand picked a technician... Ta is Incredibly intelligent, personable, professional, engaging and leaves the customer feeling that he had their best interest at heart... Comfort Control should be extremely proud to have Ta servicing their customers... if you don't already have the position, he should be made VP of Corporate Training...
Great service....has been here before ....very professional
RICH - Suwanee, GA
Bob - Suwanee, GA
Frank - Suwanee, GA
Dennis - Suwanee, GA
TAMMY - Suwanee, GA
JOHN - Suwanee, GA
Always a good experience with Comfort Control. Reece came early, but called first to verify it was ok.
Replaced icomfprt thermostat under warranty.
3 system ac renewal special. Replaced filters, cleared drain and clean coil. Added 1 lb freon for upstair,main floor and basement. Installed hardstart kit for upstair and main floor system. 3 system cooling normal
Complete cooling pm check. Find ac system operating with low charge. Find system leaking at media coil in attic. Give customer estimate to replace warranty coil. Also will need to replace weak compressor capacitor. Give customer estimate to install steam humidifier in attic.
We installed a 2 ton 60000btu systems. We added a 10â€ return in the hallway and a 6â€ supply into the sonâ€™s bedroom. The condenser was shifted about 8 foot towards the back of the home. The condenser has been leveled and set on a pad. We added new plenums and replaced the single wall flue piping with the roofer. We must replace the breaker for the condenser. We need a 30 square D breaker (QO type). Jeff will add the breaker tomorrow and check the condenserâ€™s pressures. The system comes with a 10 year parts warranty and at least a 5 year labor warranty.
ASX160241 AMVC80604BX Labor Warranty (years) (10) X Parts Warranty (years) (10) X Compressor Warranty (years) (Lifetime) X Heat Exchanger Warranty (years) (Lifetime) X Proposal Valid (days) (30) 5 inch media filter no thermostat add 1 10 inch return in hallway and 1 10 inch supply in bedroom above garage
1 system ac pm check complete. Left customer with replacement filter. Tested mechanical and electrical components, all in good shape. Chemically washed condenser coil and applied rust proof waxing. Replaced insulation on suction line outside. System is cooling at this time.
Inducer assembly blocked. Cleaned blockage and emptied debris from inducer housing. System operating properly at this time
2 furnace pm check complete. Changed media filters. Tested mechanical and electrical components. All in good shape. Systems are heating normal at this time. Insulation levels are low, recommend adding more insulation for increased comfort and efficiency.
No cool. Dog chewed through wires. Reran new wires and armaflex. Tested and working
Heating Repair: Check and find downstairs heating system failed due to locked up inducer motor. Replace inducer assembly under 10-year warranty part and labor. System operating at this time. Rerun upstairs 95% furnace drain to main ac drain system to remove water. Work under warranty. Both system heating at this time.
2 system furnace tuneup and signed for a new Comfort Club Membership. Replaced very dirty filter, checked electrical and safety switches all ok at this time. Both systems have rusty evaporator coils. Both furnaces have worn ignition, weak flame safety sensor, and weak blower motor controller. Did a combustion test on both furnaces. Upstairs all within range. Found downstairs with higher oxygen level. Recommend a combustion calibration to make furnace burn cleaner and more efficiently.
2 furnace preventative maintenance check complete. Changed filters. Dusted out furnace cabinets. Cleared barometric tubing.Upstairs system: I tested the combustion and found safe carbon monoxide levels and good oxygen levels. The system is heating at 80% efficiency, which is what the furnace is rated for. Tested furnace components and found blower motor controller running weak. Recommend repair. I tested the drain line I rebuilt in the summer and it is clear and functional.Main level system: This furnace also has safe carbon monoxide levels, good oxygen levels and is heating at 80% efficiency. The blower wheel is dirty, recommend cleaning. Tested furnace components and found worn ignition system with silica dust build up, it could break/fail at any time. Recommend repair. Aside from that, I found no mechanical issues.Replaced the main level ignition system with moisture resistant ignition system. Replaced upstairs blower motor controller. Systems are heating at this time.
Full warranty.No heat main floor zone system. Found icomfort thermostat with bad lcd. Went to Lennox and picked up the thermostat. Installed thermostat, register the thermostat, tested and system now heating normal with both zone
Heating Repair: No heat on the downstairs system. Found system with a diagnostic code (burners failed to ignite) replaced ignition and system now heating. Found weak flame safety sensor and weak blower motor controller, owner decline repair.
Sign up 1 Comfort Club Membership and complete heating preventative maintenance check. Find heating system operating with weak blower motor controller, suggest customer to replace but want to wait. Suggest surge protection for the heating system and electric. Change filter, check safety and operation.
Completed maintenance on 2 systems. Upstairs unit has very rusty evaporator coil and dirty blower motor. Main floor unit needs new air cleaner customer wants to replace themselves also main floor evaporator coil is very rusty.
2 furnace pm check complete. Changed main level media filter. Tested mechanical and electrical components, all in good shape. Systems are heating normal at this time. Renew 2 system cci plan
2 furnace pm check complete. Tested mechanical and electrical components, all in good shape. Did not change filters. Systems are heating at this time.
Installed New Heating and Air Conditioning System New condensate pump and Beckett tubing.
Installed New HVAC System with solar attic fan, 5-inch media filter with APCO, and a 10 years parts & labor lifetime compressor and heat exchanger warranty.
Upgrade both system TSTAT, test and both new APRILAIRE PROGRAMS TSTAT 8466 operating normal. Both heating system operating at this time. 5 year warranty tstat and 1 year warranty labor
Found fault in 12" damper going to master bedroom. Replaced with new and everything is operating normally at this time.
Inducer port was clogged. System is now heating
2 system furnace prepaid pm. Air cleaner is good, checked electrical and safety switches all ok at this time. Tested both system combustion and all within range and heating normal at this time. Suggest apco uv light for bacteria and mold prevention.
Check for rust at drain pan downstairs, find Drain pan have minor rusts due to water at some point from condensate pump. Test drain pan with water and did not see leak. Drain pan and water overflow protection operating normal. Drain pan still in good condition with minor rust. Need to come back for upstairs system to rerun drain line and remove condensate pump in attic. Customer want to call us back later to complete work or upstairs system. Per Tom, warranty no charge.