The residents of Braselton, GA have considered Comfort Control a dependable company for heating and cooling services since 1992. Read how we provide top quality heating and cooling practices and continue to earn five star reviews in the Braselton, GA area.
for Braselton, GA
Our Reviews by City
Good company standars
JOEY - Braselton, GA
Reece was very nice & explained things along the way. Although, it took 2 weeks before we had heat again, minus 2 days for Thanksgiving holidays. Thankfully Reece & Tom were willing to come by late in the day & stay until it was fixed.
Response from Comfort Control Heating & Air:
I am very sorry it took so long to get the parts. We are working with Trane to fix that problem. I am happy we were able to get you back up and running. Thank you for being patient with us!
JOEY - Braselton, GA
Provided Great Service
GERALD - Braselton, GA
Very efficient and arrived on time for appointment
JOSEPH - Braselton, GA
BOB - Braselton, GA
Seth was on time and completed the work in a short amount of time. He answered questions around a future new HVAC system without pressuring to do it now.
Air Conditioning repair. 1 system a/c preventative maintenance check complete. I left the customer with a replacement filter. Added chlorine tablets to evap coil drain pan and cleared drain line. Replaced 2 UV bulbs. Found weak voltage absorption system and pitted voltage distribution system, replaced both parts. Chemically washed condenser coil and applied rust proof waxing. Heating and cooling maintenance complete which will help lower cooling cost for this residential customer. Cooling system is now ready for spring and summer weather.
Checked job for install. Need to order a gas furnace from tristate. 12" flex needs to be replaced under the house . May need some 14" too.
We installed a 4 ton System. We replaced a 10â€ damper and added a 10â€ Bypass. We added a 14â€ return. We set the heat pump on new padding. The system passed all required leak tests and properly held a vacuum. We used the programmable Aprilaire Thermosats. We used a Honeywell Zoneboard. The system was temporarily sealed at the filter access port because we will return to change the 14â€ return into a 14â€ filter return. We will permantley seal the filter port at that time. I collected $8332. The system comes with a 10 year parts and labor warranties.
Performed 1 system cooling maintenance. Only one form of water safety in attic. Recommend installing inline pvc secondary switch to safeguard against leaks. System has no form of power protection. Surge protector needs to be installed to keep electrical components from damage. Flushed drain line. Added bleach to clean pvc. Tested all electrical components for normal operation.
Performed 1 system cooling maintenance. New train system. No form of power protection. Recommend installing surge protector for outdoor unit. Recommend installing hard start compressor saver kit on outdoor unit to lower amp drawl and increase the life of the condenser. Air handler only has one form of water safety. Need to install secondary water switch to safeguard against water damage if drain should ever become clogged or pan overflow. System operating properly at this time .
Performed 2 system cooling maintenance. Neither evaporator coil has inline overflow switch. Outdoor units are 12 years old compressors drawing high amp. Recommend installing hard start compressor saver kits on outdoor units. No power protection on outdoor units. Recommend installing surge protectors to keep units from electrical damage. Changed filters. Flushed drain lines. Both systems operating normal at this time.
Performed 1 system cooling maintenance. Large amounts of black mold growing in air handler, system needs u/v lighting system to kill mold spores and bacteria. Air handler has no form of power protection. Recommend installing surge protector to keep all electrical components safe from damage.
We need to return to test the system. The electrician needs to finish before we can test the system. We need to return with a 4" color, elbow, and damper so we can condition the mechanical room. He still hasn't received the green sky card. I collected the authorization signature.
We need to return after electrician to test the system and to finish the last bit. The homeowner does not have his green sky card yet.
1 ac pm check complete. Changed filter customer provided. Tested mechanical and electrical components, all in good shape. System is operating normal at this time. Chemically washed condenser coil and applied rust proof waxing.
2 heat pump HVAC maintenance check complete. Changed main level filter. Did not change the upstairs filter. The main level blower motor controller is running weak, recommend repair. Upstairs has no water safety, recommend adding on to prevent water damage to the ceiling. Found mold in the upstairs air handler, recommend APCO air purifier to kill and prevent mold and to help keep evaporator coil clean. The main level system runs on r22, a refrigerant that is being phased out by the EPA in 2020. Main level compressor and fan are operating at high amp draw. Recommend performance enhancement kit to help compressor run smoother and last longer. Systems are heating at this time. Changed main level blower motor controller to ensure reliable motor performance.
Heating and air conditioning repair: HVAC System had a faulty blower motor controller. The part was replaced System is now heating. Also, the outdoor unit had a burnt wire at the Herm (compressor) terminal to the capacitor, outdoor Coil is dirty, and also recommend a hard start kit be added. This System is becoming too costly to maintain. We recommend replacement of the equipment. A consultation has been scheduled today from 2-4.
Heating Repair: System had a faulty blower motor capacitor. The capacitor was replaced System is now heating. Also, the outdoor unit had a burnt wire at the Herm (compressor) terminal to the capacitor, outdoor Coil is dirty, and also recommend a hard start kit be added. This System is becoming too much work to maintain. We recommend replacement of the equipment. A consultation has been scheduled today from 2-4.
Performed 2 system heating maintenance. Installed pvc unions and cleaned drain line. Replaced filters. Downstairs voltage absorbsion system metering below acceptable levels and needs to be replaced. Upstairs supply plenum growing black mold. Recommend installing U/V lighting system to kill mold spores and bacteria. Neither system has drain pan switch. Recommend installing pan switches to prevent water damage in the event of a leak. Installed apco U/V light. Replaced downstairs voltage absorbsion system. Installed pan switch for each system. Both units operating properly at this time.
Heating Repair: Thermostat was not set up for a heat pump system.
Heating Repair: Completed maintenance on Westinghouse heat pump. Found bad defrost sensor and defrost board causing the heat pump to ice up and not thaw out.
We installed the Aprilaire 600M Humidifier. The system humidifier was tested and set on 35% humidity. $650 paid by check.
Performed 1 System Maintenance. System is 6 years old. Currently heating. I recommend the contactor be replaced during the spring visit. Also ask about upgrading UV system.
Performed 2 system heating maintenance. Blower wheels both need to be chemically cleaned to restore balance and efficiency. Upstairs blower wheel is priority. Flushed drain lines and added pvc unions. Checked all electrical components for proper operation. Both systems are running at this time.
System low on 410a. Thermostat not set up correctly for heat pump. System low on refrigerant due to loose connection at expansion valve.Set up thermostat correctly and charged system with 410a. System operating properly at this time.
Estimate for new humudifier
Complete 5 system heating pm check. Change all filter. Find ignition failing for upstairs, main level and kitchen furnace Find sensor weak for upstairs and main level. Suggest repair befor system fail. Overall all 5 heating system operating at this time.
Performed 1 system heating maintenance. Changed filter. Cleaned out drain line. Checked all system components for normal operation. Found large amounts of mold growth in air handler cabinet. Recommend installing U/V lighting to kill mold and bacteria. Air handler has no form of power protection. Recommend installing surge protector to keep electrical components from damage. System operating properly at this time
Replaced blower motor module, motor and board. System heating at this time. Office will call to schedule maintenance.
Need to come back to replace motor module. Did not complete repair